Refrigerant composition

ABSTRACT

Provided is a refrigerant composition that has a low GWP; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants. Specifically, provided is a refrigerant composition containing FO-1216 and a hydrofluoroolefin, wherein the hydrofluoroolefin is at least one member of HFO-1234ze and HFO-1243zf.

TECHNICAL FIELD

The present disclosure relates to a refrigerant composition, in particular a refrigerant composition that has low global warming potential (GWP); is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, and R-404A.

BACKGROUND ART

Refrigerants for use in a range of air conditioners, coolers, etc. (including working media for thermal cycling, without a limitation to those for cooling), are required to have characteristics, such as low GWP, low flammability (preferably non-flammable or mildly flammable), and high Cap and/or COP. In particular, from the standpoint of GWP, hydrofluoroolefin (HFO) refrigerants have been used as alternatives for traditional hydrofluorocarbon (HFC) refrigerants.

However, the use of an HFO refrigerant alone still leaves room for improvement in terms of flammability, although its low GWP of less than 10 is an advantage. To address these circumstances, attempts have been made to mix an HFO refrigerant with a known non-flammable refrigerant to make the entire mixture non-flammable. However, adding a known non-flammable refrigerant increases GWP. Thus, refrigerants that achieve both GWP and low flammability have yet to be developed.

There are documents related to the present disclosure. These include, for example, the following Patent Literature 1 to 4.

PTL 1 relates to a heat transfer composition, and claim 1 thereof discloses “[a] heat transfer composition comprising (i) trans-1,3,3,3-tetrafluoropropene (R-1234ze(E)), (ii) a second component selected from difluoromethane (R-32), propene (R-1270), propane (R290), and mixtures thereof, (iii) a third component selected from pentafluoroethane (R-125), 1,1,1,2-tetrafluoroethane (R-134a), and mixtures thereof, and optionally (iv) a fourth component selected from fluoroethane (R-161), 1,1-difluoroethane (R-152a), and mixtures thereof.”

The heat transfer composition of PTL 1 is a combination of R-1234ze(E), which is an HFO refrigerant, with the second component, the third component, etc. Although the composition includes a non-flammable composition (claim 22), its GWP is less than 2800, and preferably less than 1500 (claim 17). In actuality, a GWP of more than 1400 and less than 1500 is the limit.

PTL 2 relates to a fluid composition, a refrigerant composition, etc. Claim 1 thereof discloses a fluid composition that is a composition (I) comprising at least one component (A) selected from the group consisting of alkanes, halogenated alkanes, and alkenes, and at least one component (B) selected from halogenated alkenes; or a composition (II) comprising at least two components (B) selected from halogenated alkenes (excluding composition (I)), wherein the combustion inhibiting effect is at least 10%.

The composition (II) contains at least two components (B), and the component (B) includes various HFO compounds and other compounds (claim 8). The fluid composition, refrigerant composition, and the like of PTL 2 are disclosed as having a combustion-inhibiting effect of at least 10%. However, the inhibition of flammability still leaves room for improvement, and the demand for non-flammability or mild flammability is not satisfied. PTL 2 also does not suggest the quantitative relation between the components for achieving a low flammability of the entire composition.

PTL 3 relates to a working fluid (e.g., a refrigerant) containing a perfluoropropylene (hexafluoropropylene: FO-1216); and discloses on page 2, upper-right column to lower-left column, that the perfluoropropylene can be mixed with another compound having a boiling point that is different by ±50° C. from the boiling point of the perfluoropropylene, such that the amount of the other compound is up to 50% by weight of the perfluoropropylene. PTL 3 lists examples of substances that can be added, such as chlorofluorocarbons, ethers, and amines. However, PTL 3 nowhere suggests GWP of the entire mixture, or the quantitative relation between the components for achieving a low flammability.

PTL 4 relates to an alternative refrigerant containing hexafluoropropylene (FO-1216), and the claims thereof list examples of non-flammable refrigerants that are a combination of FO-1216 with another component. However, PTL 4 nowhere suggests the quantitative relation between the components aiming to reduce the GWP of the entire mixture.

CITATION LIST Patent Literature

PTL 1: JP2012-7164A

PTL 2: WO2016/182030A

PTL 3: JPH03-93888A

PTL 4: WO1998/05732A

SUMMARY OF INVENTION Technical Problem

The present disclosure has been made in view of the problems in the related art, and a major object is to provide a refrigerant composition that has a low GWP; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, and R-404A, when used as an alternative refrigerant for such traditional refrigerants.

Solution to Problem

The present inventors conducted extensive research to achieve the object, and found that a specific mixture containing FO-1216 can achieve the object. The inventors then completed the present disclosure.

Specifically, the present disclosure relates to the following refrigerant compositions.

1. A refrigerant composition comprising FO-1216 and a hydrofluoroolefin, wherein the hydrofluoroolefin is at least one member of HFO-1234ze and HFO-1243zf.

2. The refrigerant composition according to Item 1, wherein the FO-1216 is present in an amount of 2 mol % or more based on the total amount of the FO-1216 and the hydrofluoroolefin taken as 100 mol %.

3. The refrigerant composition according to Item 1 or 2, further comprising a hydrofluoroether.

4. The refrigerant composition according to Item 3, wherein the hydrofluoroether is present in an amount of 2 mol % or more based on the total amount of the hydrofluoroether, the hydrofluoroolefin, and the FO-1216 taken as 100 mol %.

5. The refrigerant composition according to Item 3 or 4, wherein the hydrofluoroether contains HFE-227me.

6. A refrigerant composition comprising FO-1216 and a halogenated ethylene.

7. The refrigerant composition according to Item 6, wherein the FO-1216 is present in an amount of 10 mol % or more based on the total amount of the FO-1216 and the halogenated ethylene taken as 100 mol %.

8. The refrigerant composition according to Item 6 or 7, wherein the halogenated ethylene is at least one member selected from the group consisting of HCFO-1122a, FO-1114, HFO-1123, HFO-1132(E), HFO-1132(Z), HFO-1132a, and HFO-1141.

9. A refrigerant composition comprising FO-1216 and a hydrofluorocarbon, wherein the FO-1216 is present in an amount of 26 mol % or more based on the total amount of the FO-1216 and the hydrofluorocarbon taken as 100 mol %.

10. The refrigerant composition according to Item 9, wherein the hydrofluorocarbon is at least one member selected from the group consisting of HFC-125, HFC-143a, HFC-32, HFC-134, HFC-134a, HFC -152a, and HFC-227ea.

11. A refrigerant composition comprising FO-1216 and at least two members selected from the group consisting of HFO-1234ze, HFO -1243zf, HFO-1234yf, a halogenated ethylene, a hydrofluorocarbon, and a hydrofluoroether.

12. The refrigerant composition according to Item 11, comprising the FO-1216 and at least two members selected from the group consisting of the HFO-1234ze, the HFO-1243zf, the HFO-1234yf, the hydrofluorocarbon, and the hydrofluoroether, wherein the FO-1216 is present in an amount of 2 mol % or more based on the total amount of the FO-1216 and at least two members selected from the group consisting of the HFO-1234ze, the HFO-1243zf, the HFO -1234yf, the hydrofluorocarbon, and the hydrofluoroether taken as 100 mol %.

13. The refrigerant composition according to Item 11, comprising the FO-1216 and at least two members selected from the group consisting of the halogenated ethylene, the hydrofluorocarbon, and the hydrofluoroether, wherein the FO-1216 is present in an amount of 30 mol % or more based on the total amount of the FO -1216 and at least two members selected from the group consisting of the halogenated ethylene, the hydrofluorocarbon, and the hydrofluoroether taken as 100 mol %.

14. The refrigerant composition according to Item 11 or 12, wherein the hydrofluoroolefin is present in an amount of 50 mol % or more.

Advantageous Effects of Invention

Being a specific mixture containing FO-1216, the refrigerant composition according to the present disclosure has a low GWP; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher (preferably 80% or higher, more preferably 90% or higher, and most preferably 100% or higher) than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants. The technical meaning of “equivalent to or higher than” as used here applies to the following.

BRIEF DESCRIPTION OF DRAWINGS

FIG. 1 is a diagram illustrating an experimental apparatus for examining flammability (flammable or non-flammable).

DESCRIPTION OF EMBODIMENTS

The following describes the refrigerant composition according to the present disclosure in detail.

The refrigerant composition according to the present disclosure is a specific mixture containing FO-1216 (hexafluoropropylene), which is suitable for use in a refrigerant (including working media for thermal cycling, without a limitation to those for cooling), has a low GWP; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

The refrigerant composition according to the present disclosure can be broadly divided into the following refrigerant compositions of embodiments 1 to 4. The technical meanings of “non-flammable” and “mildly flammable” in the present specification are as described below.

In the present specification, whether a composition is flammable or non-flammable was confirmed by performing a combustion test on a mixture refrigerant in relation to the composition ratio, based on ASTM E681 (an ASHRAE method), using a flammability experimental apparatus schematically illustrated in FIG. 1 (the following is illustrated: A. charging line, B. sampling line, C. thermometer, D. pressure gauge, E. electrodes, and F. stirring blade (made of PTFE)). A combustion angle of 90° or less was determined to be non-flammable.

A combustion angle of more than 90° was determined to be flammable based on the flammable range test. In particular, “mildly flammable” in the present specification was distinguished as compositions with a burning rate of 10 cm/s or less, among those determined to be flammable, in accordance with the burning rate test of ASHRAE 34-2010.

Refrigerant Composition of Embodiment 1

A refrigerant composition according to embodiment 1 contains FO-1216 and a hydrofluoroolefin. The hydrofluoroolefin is at least one member of HFO-1234ze (1,3,3,3-tetrafluoropropene) and HFO-1243zf (3,3,3-trifluoropropene).

The refrigerant composition according to embodiment 1 preferably contains FO-1216 in an amount of 2 mol % or more based on the total amount of FO-1216 and the hydrofluoroolefin (hereinafter, “the hydrofluoroolefin” refers to at least one member of HFO-1234ze and HFO-1243zf) taken as 100 mol %.

The refrigerant composition according to embodiment 1 contains an HFO refrigerant as the main refrigerant. Being a mixture of FO-1216 and the hydrofluoroolefin, the refrigerant composition has a low GWP (preferably 300 or lower); is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R -410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants. FO-1216 is a non-flammable substance in the present specification, and is positioned as a flammability-reducing agent (this position applies to the refrigerant compositions of other embodiments).

Regarding the content of FO-1216 and the hydrofluoroolefin, FO-1216 is preferably present in an amount of 2 mol % or more based on the total amount of FO-1216 and the hydrofluoroolefin taken as 100 mol %; in other words, the hydrofluoroolefin is preferably present in an amount of 98 mol % or less based on the total amount of FO-1216 and the hydrofluoroolefin taken as 100 mol %. In particular, it is more preferred that FO-1216 be present in an amount of 90 to 10 mol %, and that the hydrofluoroolefin be present in an amount of 10 to 90 mol %. A refrigerant composition containing FO-1216 and the hydrofluoroolefin in an amount within these numerical ranges can easily have a low GWP (in particular 10 or less); become non-flammable or mildly flammable; and have a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

The refrigerant composition according to embodiment 1 preferably has a GWP of 300 or lower, and more preferably 150 or lower. Although FO-1216 is positioned as a flammability-reducing agent that makes the entire composition non-flammable in the refrigerant composition according to embodiment 1, the refrigerant composition may also contain other flammability-reducing agents in combination, as long as the composition contains FO-1216 as an essential element, and the effects of the present disclosure are not impaired.

Further adding a hydrofluoroether (HFE) to the refrigerant composition according to embodiment 1 imparts the following characteristics to the refrigerant composition: even if the refrigerant composition leaks from a refrigerant pipe, the refrigerant composition remaining inside the pipe can easily maintain the non-flammable characteristics, while maintaining the low-GWP characteristics (300 or lower). HEE for use is a non-flammable substance in the present specification. Regarding the content of HFE, HFE is preferably present in an amount of 2 mol % or more based on the total amount of HFE, the hydrofluoroolefin, and FO-1216 taken as 100 mol %.

HFE is, for example, at least one member of trifluoromethyl 1,2,2,2-tetrafluoroethyl ether (HFE-227me), difluoromethyl 1,1,2,2,2-pentafluoroethyl ether (HEE-227mc), trifluoromethyl 1,1,2,2-tetrafluoroethyl ether (HFE-227pc), difluoromethyl 2,2,2-trifluoroethylether (HFE-245mf), and 2,2-difluoroethyltrifluoromethyl ether (HFE-245pf). In particular, HFE-227me is preferable.

For example, the use of HFO-1234ze (boiling point: about −19° C.) as the hydrofluoroolefin, and HFE-227me (boiling point: about −10° C.) together with FO-1216 (boiling point: about −30° C.) in the refrigerant composition according to embodiment 1 imparts to the resulting composition characteristics such that even if the refrigerant composition leaks from a refrigerant pipe, the refrigerant composition remaining inside the pipe can easily maintain the non-flammable characteristics, while maintaining the low-GWP characteristics (300 or lower).

This is due to the fact that even if a refrigerant composition leaks from a refrigerant pipe, combining a flammable HFO refrigerant (e.g., HFO-1234ze: the main refrigerant) with a non-flammable refrigerant that has a lower boiling point than the main refrigerant (FO-1216) and a non-flammable refrigerant that has a higher boiling point than the main refrigerant (e.g., HFE-227me) allows the non-flammable refrigerant that has a lower boiling point than the main refrigerant to leak first, leaving the non-flammable refrigerant that has a higher boiling point than the main refrigerant, and thus maintaining the non-flammable characteristics of the refrigerant composition remaining inside the refrigerant pipe.

In this case, the non-flammable refrigerant that has a lower boiling point than the main refrigerant (FO-1216) is preferably present in an amount of 1 mol % or more in the refrigerant composition (before leak), and the non-flammable refrigerant that has a higher boiling point than the main refrigerant (e.g., HFE-227me) is preferably present in an amount of 1 mol % or more in the refrigerant composition (before leak). The difference in boiling point between the non-flammable refrigerant having a lower boiling point than the main refrigerant and the main refrigerant is preferably 5° C. or more, and more preferably 5 to 15° C. The difference in boiling point between the non-flammable refrigerant having a higher boiling point than the main refrigerant and the main refrigerant is preferably 5° C. or more, and more preferably 5 to 15° C.

From the viewpoint above, the present disclosure includes a refrigerant composition such that even if the refrigerant composition leaks from a refrigerant pipe, the refrigerant composition maintains its non-flammable characteristics. More specifically, the present disclosure also includes “a refrigerant composition that contains a flammable HFO refrigerant as the main refrigerant, 1 mol % or more of HFO-1216 (non-flammable refrigerant) having a lower boiling point than the flammable HFO, and 1 mol % or more of a non-flammable refrigerant having a higher boiling point than the flammable HFO.” The HFO refrigerant as used here is not limited to the hydrofluoroolefin according to embodiment 1, and a wide range of known HFO refrigerants are applicable.

Refrigerant Composition of Embodiment 2

A refrigerant composition according to embodiment 2 contains FO-1216 and a halogenated ethylene.

The refrigerant composition according to embodiment 2 preferably contains FO-1216 in an amount of 10 mol % or more based on the total amount of FO-1216 and the halogenated ethylene taken as 100 mol %.

Being a mixture of FO-1216 and the halogenated ethylene, the refrigerant composition according to embodiment 2 has an extremely low GWP of 1 or less; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

The halogenated ethylene is, although not limited thereto, for example, at least one member selected from the group consisting of HCFO-1122a (CFH═CFCl), FO-1114 (CF₂═CF₂), FIFO-1123 (CF₂═CFH), HFO-1132 (E) (trans-CFH═CFH), HFO-1132 (Z) (cis-CFH═CFH), HFO-1132a (CH₂═CF₂), and HFO-1141 (CH₂═CFH). Of these, from the standpoint of refrigerating capacity and coefficient of performance, at least one member of FO-1114, HFO-1132(E), and HFO-1123 is particularly preferable.

Regarding the content of FO-1216 and the halogenated ethylene, FO-1216 is preferably present in an amount of 10 mol % or more based on the total amount of FO-1216 and the halogenated ethylene taken as 100 mol %; in other words, the halogenated ethylene is preferably present in an amount of 90 mol % or less based on the total amount of FO-1216 and the halogenated ethylene taken as 100 mol %. In particular, it is more preferred that FO-1216 be present in an amount of 90 to 50 mol %, and that the halogenated ethylene be present in an amount of 10 to 50 mol %. A refrigerant composition containing FO-1216 and the halogenated ethylene in an amount within these numerical ranges can easily become non-flammable or mildly flammable; and have a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

Although FO-1216 is positioned as a flammability-reducing agent that makes the entire composition non-flammable in the refrigerant composition according to embodiment 2, the refrigerant composition may also contain other flammability-reducing agents in combination, as long as the composition contains FO-1216 as an essential element, and the effects of the present disclosure are not impaired.

Refrigerant Composition of Embodiment 3

A refrigerant composition according to embodiment 3 contains FO-1216 and a hydrofluorocarbon (HFC). The composition contains FO-1216 in an amount of 26 mol % or more based on the total amount of FO-1216 and the hydrofluorocarbon taken as 100 mol %.

Being a mixture of FO-1216 and the hydrofluorocarbon, the refrigerant composition according to embodiment 3 has a low GWP (preferably 600 or lower, and more preferably 300 or lower); is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

The hydrofluorocarbon (HFC) is, although not limited thereto, for example, at least one member of 1,1,2,2,2-pentafluoroethane (HFC-125), 1,1,1-trifluoroethane (HFC-143a), difluoromethane (HFC-32), 1,1,2,2-tetrafluoroethane (HFC-134), 1,1,1,2-tetrafluoroethane (HFC-134a), 1,1-difluoroethane (HFC-152a), and 1,1,1,2,3,3,3-heptafluoropropane (HFC-227ea). Of these, from the standpoint of refrigerating capacity and coefficient of performance, HFC-32 is preferable. From the standpoint of non-flammability, at least one member of HFC-125, HFC-134, HFC-134a, and HFC-227ea is preferable.

Regarding the content of FO-1216 and the hydrofluorocarbon, FO-1216 may be present in an amount of, for example, 26 mol % or more based on the total amount of FO-1216 and the hydrofluorocarbon taken as 100 mol %; in other words, the hydrofluorocarbon may be present in an amount of, for example, 74 mol % or less based on the total amount of FO-1216 and the hydrofluorocarbon taken as 100 mol %. In particular, it is more preferred that FO-1216 be present in an amount of 90 to 30 mol %, and that the hydrofluorocarbon be present in an amount of 10 to 70 mol %. A refrigerant composition containing FO-1216 and the hydrofluorocarbon in an amount within these numerical ranges can easily have a low GWP (600 or lower, in particular 300 or lower); be non-flammable or mildly flammable; and have a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

The refrigerant composition according to embodiment 3 preferably has a GWP of 300 or lower, and more preferably 150 or lower.

Although FO-1216 is positioned as a flammability-reducing agent that makes the entire composition non-flammable in the refrigerant composition according to embodiment 3, the refrigerant composition may also contain other flammability-reducing agents in combination, as long as the composition contains FO-1216 as an essential element, and the effects of the present disclosure are not impaired.

Refrigerant Composition of Embodiment 4

A refrigerant composition according to embodiment 4 contains FO-1216 and at least two members selected from the group consisting of HFO-1234ze, HFO-1243zf, HFO-1234yf, a halogenated ethylene, a hydrofluorocarbon (HFC), and a hydrofluoroether (HFE).

The refrigerant composition according to embodiment 4 preferably contains FO-1216 in an amount of 2 mol % or more based on the total amount of FO-1216 and at least two members selected from the group consisting of HFO-1234ze, HFO-1243zf, HFO-1234yf, a hydrofluorocarbon, and a hydrofluoroether (simply “other component A”) taken as 100 mol %.

The refrigerant composition according to embodiment 4 preferably contains FO-1216 in an amount of 30 mol % or more based on the total amount of FO-1216 and at least two members selected from the group consisting of a halogenated ethylene, a hydrofluorocarbon, and a hydrofluoroether (simply “other component B”) taken as 100 mol %.

Being a mixture of FO-1216 and other component A or B, the refrigerant composition according to embodiment 4 has a low GWP (preferably 300 or lower); is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

The halogenated ethylene for use may be those listed in embodiment 2. More specifically, the halogenated ethylene is, for example, at least one member selected from the group consisting of HCFO-1122a (CFH═CFCl), FO-1114 (CF₂═CF₂), HFO-1123 (CF₂═CFH), HFO-1132(E) (trans-CFH═CFH), HFO-1132(Z) (cis-CFH═CFH), HFO-1132a (CH₂═CF₂), and HFO-1141 (CH₂═CFH). Of these, from the standpoint of refrigerating capacity and coefficient of performance, at least one member of HFO-1132(E) and HFO-1123 is particularly preferable.

The hydrofluorocarbon (HFC) for use may be those listed in embodiment 3. More specifically, the hydrofluorocarbon is, for example, at least one member of 1,1,2,2,2-pentafluoroethane (HFC-125), 1,1,1-trifluoroethane (HFC-143a), difluoromethane (HFC-32), 1,1,2,2-tetrafluoroethane (HFC-134), 1,1,1,2-tetrafluoroethane (HFC-134a), 1,1-difluoroethane (HFC-152a), and 1,1,1,2,3,3,3-heptafluoropropane (HFC-227ea). Of these, from the standpoint of refrigerating capacity and coefficient of performance, R32 is preferable. From the standpoint of non-flammability, at least one member of HFC-134, HFC-134a, and HFC-227ea is preferable.

The hydrofluoroether (HFE) for use may be those listed in embodiment 1. More specifically, HFE is, for example, at least one member of trifluoromethyl 1,2,2,2-tetrafluoroethyl ether (HFE-227me), difluoromethyl 1,1,2,2,2-pentafluoroethyl ether (HFE-227mc), trifluoromethyl 1,1,2,2-tetrafluoroethyl ether (HFE-227pc), difluoromethyl 2,2,2-trifluoroethylether (HFE-245mf), and 2,2-difluoroethyltrifluoromethyl ether (HEE-245pf). In particular, HFE-227me is preferable.

Regarding the content of FO-1216 and at least two members selected from the group consisting of HFO-1234ze, HFO-1243zf, HFO-1234yf, a hydrofluorocarbon (HFC), and a hydrofluoroether (HFE), FO-1216 is preferably present in an amount of 2 mol % or more based on the total amount of FO-1216 and other component A taken as 100 mol %; in other words, other component A is preferably present in an amount of 98 mol % or less based on the total amount of FO-1216 and other component A taken as 100 mol %. In particular, it is preferred that FO-1216 be present in an amount of 10 to 2 mol %, and that other component A be present in an amount of 90 to 98 mol %.

Regarding the content of FO-1216 and at least two members selected from the group consisting of a halogenated ethylene, a hydrofluorocarbon (HFC), and a hydrofluoroether (HFE), FO-1216 is preferably present in amount of 30 mol % or more based on the total amount of FO-1216 and other component B taken as 100 mol %; in other words, other component B is preferably present in an amount of 70 mol % or less based on the total amount of FO-1216 and other component B taken as 100 mol %. In particular, it is more preferred that FO-1216 be present in an amount of 70 to 30 mol %, and that other component B be present in an amount of 30 to 70 mol %.

A refrigerant composition containing FO-1216 and the at least two members in an amount within these numerical ranges can easily have a low GWP (300 or lower, in particular 200 or lower); become non-flammable or mildly flammable; and have a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

Additives usable for the refrigerant composition according to the present disclosure, and the scope of application of the refrigerant composition according to the present disclosure

The refrigerant composition according to the present disclosure (refrigerant compositions according to embodiments 1 to 4) may optionally contain additives when used in a refrigerant. Examples of additives include stabilizers, refrigerant oils, corrosion inhibitors, rust retardants, lubricants, polymerization inhibitors, solvents, and water.

Examples of stabilizers include aliphatic nitro compounds, such as nitromethane and nitroethane; ethers, such as 1,4-dioxane; amines, such as 2,2,3,3,3-pentafluoropropylamine, and diphenylamine butyl hydroxyxylene; and benzotriazole. Stabilizers may be used singly, or in a combination of two or more. Examples of refrigerant oils for use include, although not limited thereto, polyalkylene glycols, polyol esters, polyvinyl ethers, and alkyl benzene mineral oils. Examples of polymerization inhibitors include 4-methoxy-1-naphthol hydroquinone, hydroquinone methyl ether, dimethyl-tert--butylphenol, 2,6-di-tert-butyl-p-cresol, and benzotriazole.

The amount of individual additive is not limited. For example, a polymerization inhibitor can be added in an amount of 0.01 to 5.0 mass % based on the total mass of the refrigerant composition according to the present disclosure.

The refrigerant composition according to the present disclosure as is, or the composition containing optional additives as described above, can be used in a range of equipment, such as air-conditioners and coolers. Such equipment is not limited, and the refrigerant composition is applicable to large-scale applied equipment as well as to household equipment (for general use).

Examples of applied equipment include large air conditioners and industrial process coolers, including room air conditioners, packaged air conditioners for stores, packaged air conditioners for buildings, packaged air conditioners for facilities, separate air conditioners connected with one or more indoor units and outdoor units through a refrigerant window air conditioners, portable air conditioners, rooftop or central air conditioners that send cool or warm air through a duct, gas engine heat pumps, air conditioners for trains, air conditioners for automobiles, built-in showcases, separate showcases, refrigerator-freezers for businesses, ice machines, integrated refrigerating machines, vending machines, automobile air-conditioners, refrigerating machines for cooling containers or refrigerators such as for marine shipping, chiller units, turbo refrigerating machines, and apparatuses exclusively used for a heating cycle. Examples of apparatuses exclusively used for a heating cycle include water-heating devices, floor-heating devices, and snow-melting devices.

The refrigerant composition according to the present disclosure has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of particularly traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

Specifically, when the refrigerant composition according to the present disclosure is used as an alternative refrigerant in a large air conditioner using R-134a as a refrigerant (“R-134a large air conditioner”), an air conditioner using R-410A as a refrigerant (“R-410A air conditioner”), a large air conditioner using R-123 as a refrigerant (“R-123 large air conditioner”), or a refrigerating machine or refrigerator-freezer using R-404A as a refrigerant (“R-404A refrigerating machine (refrigerator-freezer)”), the composition has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of these refrigerants.

In the present specification, the operation conditions for the R-134a large air conditioner, R-410A air conditioner, R-123 large air conditioner, and R-404A refrigerating machine (refrigerator-freezer) are as follows.

R-134a Large Air Conditioner

-   -   Evaporating temperature: 0° C.     -   Condensation temperature: 40° C.     -   Degree of superheating: 5° C.     -   Degree of subcooling: 0° C.

R-410A Air Conditioner

-   -   Evaporating temperature: 0° C.     -   Condensation temperature: 45° C.     -   Degree of superheating: 0° C.     -   Degree of subcooling: 0° C.

R-123 Large Air Conditioner

-   -   Evaporating temperature: 5° C.     -   Condensation temperature: 40° C.     -   Degree of superheating: 5° C.     -   Degree of subcooling: 5° C.

R-404A Refrigerating Machine (Refrigerator-Freezer)

-   -   Evaporating temperature: −40° C.     -   Condensation temperature: 40° C.     -   Degree of superheating: 20° C.     -   Degree of subcooling: 0° C.

EXAMPLES

The following shows the flammability and GWP of specific refrigerant compositions according to embodiments 1 to 4 in relation to the content of FO-1216 (molar ratio); and also shows the relative refrigerating capacity (Cap) and the relative coefficient of performance (COP) when each refrigerant composition was used as an alternative refrigerant in an R-134a large air conditioner, an R-410A air conditioner, an R-123 large air conditioner, or an R-404A refrigerating machine (refrigerator-freezer). Tables 1-1-1 to 4-4 illustrate the results.

Embodiment 1-1 (FO1216+HFO1234ze)

TABLE 1-1-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (mildly flammable) 0.741 0.997 6 0.1 (non-flammable) 0.775 0.987 5 0.2 (non-flammable) 0.805 0.978 5 0.3 (non-flammable) 0.834 0.969 4 0.4 (non-flammable) 0.859 0.959 4 0.5 (non-flammable) 0.882 0.949 3 0.6 (non-flammable) 0.902 0.939 3 0.7 (non-flammable) 0.918 0.930 2 0.8 (non-flammable) 0.931 0.921 2 0.9 (non-flammable) 0.941 0.910 1 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.4 to 0.9 (40 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 1-1-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410a COP vs. R410a GWP (Comparison) R410a 1.000 1.000 2088 0 (mildly flammable) 0.320 1.075 6 0.1 (non-flammable) 0.333 1.062 5 0.2 (non-flammable) 0.345 1.048 5 0.3 (non-flammable) 0.355 1.034 4 0.4 (non-flammable) 0.365 1.021 4 0.5 (non-flammable) 0.372 1.007 3 0.54 (non-flammable) 0.375 1.001 3 0.55 (non-flammable) 0.376 1.000 3 0.56 (non-flammable) 0.376 0.998 3 0.6 (non-flammable) 0.379 0.993 3 0.7 (non-flammable) 0.384 0.979 2 0.8 (non-flammable) 0.388 0.966 2 0.9 (non-flammable) 0.390 0.953 1 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.1 to 0.54 (10 to 54 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 1-1-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (mildly flammable) 4.753 0.949 6 0.1 (non-flammable) 4.984 0.944 5 0.2 (non-flammable) 5.195 0.938 5 0.3 (non-flammable) 5.393 0.932 4 0.4 (non-flammable) 5.570 0.926 4 0.5 (non-flammable) 5.732 0.920 3 0.6 (non-flammable) 5.876 0.913 3 0.7 (non-flammable) 5.999 0.907 2 0.8 (non-flammable) 6.103 0.902 2 0.9 (non-flammable) 6.185 0.896 1 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.2 to 0.8 (20 to 80 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 1-1-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (mildly flammable) 0.369 1.130 6 0.1 (non-flammable) 0.386 1.111 5 0.2 (non-flammable) 0.402 1.094 5 0.3 (non-flammable) 0.418 1.076 4 0.4 (non-flammable) 0.433 1.058 4 0.5 (non-flammable) 0.446 1.040 3 0.6 (non-flammable) 0.459 1.022 3 0.7 (non-flammable) 0.469 1.005 2 0.72 (non-flammable) 0.471 1.001 2 0.73 (non-flammable) 0.472 1.000 2 0.8 (non-flammable) 0.477 0.988 2 0.9 (non-flammable) 0.482 0.971 1 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.1 to 0.72 (10 to 72 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 1-2 (FO1216+HFO1243zf)

TABLE 1-2-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (mildly flammable) 0.825 1.005 1 0.1 (mildly flammable) 0.863 1.002 1 0.11 (mildly flammable) 0.866 1.001 1 0.12 (mildly flammable) 0.869 1.000 1 0.13 (mildly flammable) 0.872 0.999 1 0.2 (mildly flammable) 0.892 0.989 1 0.3 (mildly flammable) 0.913 0.970 1 0.4 (mildly flammable) 0.928 0.950 1 0.5 (non-flammable) 0.939 0.931 1 0.6 (non-flammable) 0.948 0.915 1 0.7 (non-flammable) 0.956 0.906 1 0.8 (non-flammable) 0.964 0.902 1 0.9 (non-flammable) 0.971 0.905 1 1 (non-flammable) 0.979 0.912 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 1-2-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (mildly flammable) 0.356 1.105 1 0.1 (mildly flammable) 0.371 1.096 1 0.2 (mildly flammable) 0.381 1.077 1 0.3 (mildly flammable) 0.388 1.051 1 0.4 (mildly flammable) 0.392 1.024 1 0.5 (non-flammable) 0.395 1.000 1 0.51 (non-flammable) 0.395 0.997 1 0.52 (non-flammable) 0.395 0.995 1 0.53 (non-flammable) 0.395 0.993 1 0.6 (non-flammable) 0.397 0.980 1 0.7 (non-flammable) 0.398 0.967 1 0.8 (non-flammable) 0.400 0.961 1 0.9 (non-flammable) 0.402 0.961 1 1 (non-flammable) 0.404 0.968 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 1-2-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (mildly flammable) 5.275 0.949 1 0.1 (mildly flammable) 5.559 0.954 1 0.2 (mildly flammable) 5.781 0.947 1 0.3 (mildly flammable) 5.949 0.933 1 0.4 (mildly flammable) 6.076 0.917 1 0.5 (non-flammable) 6.175 0.901 1 0.6 (non-flammable) 6.255 0.888 1 0.7 (non-flammable) 6.326 0.881 1 0.8 (non-flammable) 6.391 0.880 1 0.9 (non-flammable) 6.451 0.884 1 1 (non-flammable) 6.504 0.892 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 1-2-4 R4O4A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (mildly flammable) 0.444 1.199 1 0.1 (mildly flammable) 0.452 1.175 1 0.2 (mildly flammable) 0.457 1.146 1 0.3 (mildly flammable) 0.460 1.115 1 0.4 (mildly flammable) 0.462 1.085 1 0.5 (non-flammable) 0.464 1.059 1 0.6 (non-flammable) 0.466 1.037 1 0.7 (non-flammable) 0.469 1.023 1 0.8 (non-flammable) 0.474 1.015 1 0.9 (non-flammable) 0.481 1.014 1 1 (non-flammable) 0.489 1.019 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-1 (FO1216+HCFO1122a)

TABLE 2-1-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (mildly flammable) 0.556 1.073 1 0.1 (mildly flammable) 0.675 1.186 1 0.2 (mildly flammable) 0.774 1.244 1 0.3 (mildly flammable) 0.847 1.242 1 0.4 (mildly flammable) 0.895 1.195 1 0.5 (non-flammable) 0.924 1.125 1 0.6 (non-flammable) 0.939 1.051 1 0.65 (non-flammable) 0.944 1.018 1 0.68 (non-flammable) 0.947 1.000 1 0.69 (non-flammable) 0.948 0.995 1 0.7 (non-flammable) 0.948 0.989 1 0.8 (non-flammable) 0.956 0.946 1 0.9 (non-flammable) 0.966 0.921 1 1 (non-flammable) 0.979 0.912 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-1-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (mildly flammable) 0.248 1.209 1 0.1 (mildly flammable) 0.297 1.314 1 0.2 (mildly flammable) 0.339 1.361 1 0.3 (mildly flammable) 0.369 1.350 1 0.4 (mildly flammable) 0.388 1.294 1 0.5 (non-flammable) 0.397 1.215 1 0.6 (non-flammable) 0.400 1.133 1 0.7 (non-flammable) 0.401 1.063 1 0.8 (non-flammable) 0.401 1.012 1 0.82 (non-flammable) 0.401 1.005 1 0.83 (non-flammable) 0.401 1.001 1 0.84 (non-flammable) 0.401 0.998 1 0.9 (non-flammable) 0.402 0.982 1 1 (non-flammable) 0.404 0.968 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-1-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (mildly flammable) 3.496 0.989 1 0.1 (mildly flammable) 4.320 1.130 1 0.2 (mildly flammable) 4.991 1.206 1 0.3 (mildly flammable) 5.473 1.209 1 0.4 (mildly flammable) 5.795 1.162 1 0.5 (non-flammable) 5.999 1.090 1 0.6 (non-flammable) 6.126 1.017 1 0.62 (non-flammable) 6.146 1.004 1 0.63 (non-flammable) 6.155 0.997 1 0.65 (non-flammable) 6.173 0.985 1 0.7 (non-flammable) 6.216 0.958 1 0.8 (non-flammable) 6.301 0.918 1 0.9 (non-flammable) 6.397 0.898 1 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-1-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (mildly flammable) 0.282 1.320 1 0.1 (mildly flammable) 0.326 1.361 1 0.2 (mildly flammable) 0.366 1.366 1 0.3 (mildly flammable) 0.399 1.344 1 0.4 (mildly flammable) 0.425 1.299 1 0.5 (non-flammable) 0.442 1.239 1 0.6 (non-flammable) 0.453 1.174 1 0.7 (non-flammable) 0.461 1.115 1 0.8 (non-flammable) 0.469 1.069 1 0.9 (non-flammable) 0.478 1.037 1 1 (non-flammable) 0.489 1.019 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.9 (50 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-2 (FO1216+FO1114)

TABLE 2-2-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0.71 (non-flammable) 1.876 1.288 1 0.72 (non-flammable) 1.840 1.277 1 0.73 (non-flammable) 1.804 1.266 1 0.74 (non-flammable) 1.768 1.254 1 0.75 (non-flammable) 1.733 1.242 1 0.8 (non-flammable) 1.557 1.176 1 0.85 (non-flammable) 1.391 1.108 1 0.9 (non-flammable) 1.238 1.039 1 0.91 (non-flammable) 1.209 1.026 1 0.92 (non-flammable) 1.181 1.012 1 0.93 (non-flammable) 1.153 0.999 1 0.94 (non-flammable) 1.127 0.986 1 0.95 (non-flammable) 1.100 0.973 1 1 (non-flammable) 0.979 0.912 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.71 to 0.95 (71 to 95 mol %), and more preferably 0.71 to 0.92 (71 to 92 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-2-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0.77 (non-flammable) 0.667 1.228 1 0.78 (non-flammable) 0.654 1.217 1 0.79 (non-flammable) 0.641 1.206 1 0.8 (non-flammable) 0.628 1.195 1 0.85 (non-flammable) 0.564 1.138 1 0.9 (non-flammable) 0.505 1.080 1 0.95 (non-flammable) 0.452 1.023 1 0.96 (non-flammable) 0.442 1.012 1 0.97 (non-flammable) 0.432 1.001 1 1 (non-flammable) 0.404 0.968 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.77 to 0.97 (77 to 97 mol %), and more preferably 0.77 to 0.9 (77 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-2-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0.71 (non-flammable) 12.890 1.390 1 0.72 (non-flammable) 12.644 1.375 1 0.73 (non-flammable) 12.396 1.359 1 0.74 (non-flammable) 12.148 1.342 1 0.75 (non-flammable) 11.900 1.325 1 0.8 (non-flammable) 10.666 1.235 1 0.85 (non-flammable) 9.476 1.141 1 0.9 (non-flammable) 8.370 1.051 1 0.91 (non-flammable) 8.161 1.033 1 0.92 (non-flammable) 7.957 1.016 1 0.93 (non-flammable) 7.758 0.999 1 0.94 (non-flammable) 7.564 0.983 1 0.95 (non-flammable) 7.375 0.967 1 1 (non-flammable) 6.504 0.892 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.71 to 0.95 (71 to 95 mol %), and more preferably 0.71 to 0.92 (71 to 92 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-2-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0.71 (non-flammable) 0.887 1.198 1 0.72 (non-flammable) 0.869 1.194 1 0.73 (non-flammable) 0.852 1.190 1 0.74 (non-flammable) 0.834 1.186 1 0.75 (non-flammable) 0.818 1.182 1 0.8 (non-flammable) 0.738 1.158 1 0.85 (non-flammable) 0.666 1.130 1 0.9 (non-flammable) 0.601 1.097 1 0.95 (non-flammable) 0.542 1.060 1 1 (non-flammable) 0.489 1.019 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.71 to 0.95 (71 to 95 mol %), and more preferably 0.71 to 0.75 (71 to 75 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-3 (FO1216+HFO1123)

TABLE 2-3-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (mildly flammable) 2.473 0.828 1 0.1 (mildly flammable) 2.247 0.839 1 0.2 (mildly flammable) 2.047 0.850 1 0.3 (mildly flammable) 1.869 0.862 1 0.4 (mildly flammable) 1.706 0.872 1 0.5 (non-flammable) 1.554 0.880 1 0.6 (non-flammable) 1.416 0.887 1 0.7 (non-flammable) 1.286 0.892 1 0.8 (non-flammable) 1.165 0.896 1 0.9 (non-flammable) 1.052 0.900 1 0.94 (non-flammable) 1.010 0.901 1 0.95 (non-flammable) 0.999 0.902 1 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.95 (10 to 95 mol %), and more preferably 0.5 to 0.94 (50 to 94 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-3-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (mildly flammable) 1.019 0.850 1 0.1 (mildly flammable) 0.929 0.867 1 0.2 (mildly flammable) 0.847 0.882 1 0.3 (mildly flammable) 0.773 0.896 1 0.4 (mildly flammable) 0.705 0.907 1 0.5 (non-flammable) 0.642 0.917 1 0.6 (non-flammable) 0.584 0.924 1 0.7 (non-flammable) 0.530 0.930 1 0.8 (non-flammable) 0.480 0.934 1 0.9 (non-flammable) 0.434 0.938 1 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.7 (50 to 70 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-3-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (mildly flammable) 15.938 0.819 1 0.1 (mildly flammable) 14.509 0.827 1 0.2 (mildly flammable) 13.261 0.838 1 0.3 (mildly flammable) 12.152 0.849 1 0.4 (mildly flammable) 11.137 0.860 1 0.5 (non-flammable) 10.189 0.869 1 0.6 (non-flammable) 9.313 0.876 1 0.7 (non-flammable) 8.486 0.882 1 0.8 (non-flammable) 7.695 0.885 1 0.9 (non-flammable) 6.948 0.888 1 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.8 (50 to 80 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-3-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (mildly flammable) 1.708 0.912 1 0.1 (mildly flammable) 1.457 0.916 1 0.2 (mildly flammable) 1.259 0.923 1 0.3 (mildly flammable) 1.098 0.929 1 0.36 (mildly flammable) 1.014 0.933 1 0.37 (mildly flammable) 1.000 0.934 1 0.38 (mildly flammable) 0.987 0.935 1 0.4 (mildly flammable) 0.963 0.936 1 0.5 (non-flammable) 0.849 0.942 1 0.6 (non-flammable) 0.753 0.947 1 0.7 (non-flammable) 0.672 0.952 1 0.8 (non-flammable) 0.601 0.956 1 0.9 (non-flammable) 0.539 0.957 1 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.5 to 0.8 (50 to 80 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-4 (FO1216+HFO1132(E))

TABLE 2-4-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (flammable) 2.261 0.905 1 0.1 (mildly flammable) 2.075 0.907 1 0.2 (mildly flammable) 1.910 0.908 1 0.3 (mildly flammable) 1.759 0.909 1 0.4 (mildly flammable) 1.620 0.910 1 0.5 (mildly flammable) 1.491 0.911 1 0.6 (non-flammable) 1.371 0.911 1 0.7 (non-flammable) 1.257 0.909 1 0.8 (non-flammable) 1.147 0.907 1 0.9 (non-flammable) 1.045 0.907 1 0.94 (non-flammable) 1.006 0.905 1 0.945 (non-flammable) 1.000 0.904 1 0.95 (non-flammable) 0.996 0.904 1 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.95 (10 to 95 mol %), and more preferably 0.6 to 0.94 (60 to 94 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-4-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (flammable) 0.976 0.968 1 0.1 (mildly flammable) 0.890 0.966 1 0.2 (mildly flammable) 0.815 0.965 1 0.3 (mildly flammable) 0.746 0.964 1 0.4 (mildly flammable) 0.683 0.962 1 0.5 (mildly flammable) 0.626 0.960 1 0.6 (non-flammable) 0.573 0.957 1 0.7 (non-flammable) 0.523 0.953 1 0.8 (non-flammable) 0.476 0.949 1 0.9 (non-flammable) 0.432 0.945 1 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.6 to 0.9 (60 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-4-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (flammable) 14.127 0.870 1 0.1 (mildly flammable) 13.055 0.873 1 0.2 (mildly flammable) 12.095 0.877 1 0.3 (mildly flammable) 11.209 0.881 1 0.4 (mildly flammable) 11.046 0.877 1 0.5 (mildly flammable) 9.626 0.888 1 0.6 (non-flammable) 8.907 0.890 1 0.7 (non-flammable) 8.211 0.892 1 0.8 (non-flammable) 7.529 0.892 1 0.9 (non-flammable) 6.877 0.891 1 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.6 to 0.9 (60 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-4-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (flammable) 1.655 1.039 1 0.1 (mildly flammable) 1.452 1.035 1 0.2 (mildly flammable) 1.278 1.029 1 0.3 (mildly flammable) 1.125 1.022 1 0.39 (mildly flammable) 1.004 1.015 1 0.4 (mildly flammable) 0.991 1.014 1 0.5 (mildly flammable) 0.874 1.005 1 0.54 (mildly flammable) 0.833 1.001 1 0.55 (non-flammable) 0.822 1.000 1 0.56 (non-flammable) 0.811 0.999 1 0.6 (non-flammable) 0.773 0.995 1 0.7 (non-flammable) 0.685 0.985 1 0.8 (non-flammable) 0.608 0.976 1 0.9 (non-flammable) 0.542 0.966 1 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.6 to 0.9 (60 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-5 (FO1216+HFO1132(Z))

TABLE 2-5-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (flammable) 1.004 1.042 1 0.1 (mildly flammable) 1.075 1.055 1 0.2 (mildly flammable) 1.109 1.035 1 0.28 (mildly flammable) 1.118 1.007 1 0.29 (mildly flammable) 1.118 1.003 1 0.3 (mildly flammable) 1.118 0.999 1 0.4 (mildly flammable) 1.112 0.963 1 0.5 (mildly flammable) 1.099 0.935 1 0.6 (non-flammable) 1.082 0.919 1 0.7 (non-flammable) 1.064 0.912 1 0.8 (non-flammable) 1.042 0.912 1 0.9 (non-flammable) 1.014 0.913 1 1 (non-flammable) 0.979 0.912 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.6 to 0.9 (60 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-5-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (flammable) 0.448 1.173 1 0.1 (mildly flammable) 0.475 1.177 1 0.2 (mildly flammable) 0.487 1.147 1 0.3 (mildly flammable) 0.487 1.101 1 0.4 (mildly flammable) 0.480 1.055 1 0.5 (mildly flammable) 0.470 1.019 1 0.56 (non-flammable) 0.463 1.003 1 0.57 (non-flammable) 0.462 1.000 1 0.58 (non-flammable) 0.461 0.998 1 0.6 (non-flammable) 0.459 0.994 1 0.7 (non-flammable) 0.447 0.981 1 0.8 (non-flammable) 0.435 0.976 1 0.9 (non-flammable) 0.421 0.973 1 1 (non-flammable) 0.404 0.968 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.56 to 0.9 (56 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-5-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (flammable) 6.247 0.963 1 0.1 (mildly flammable) 6.757 0.988 1 0.2 (mildly flammable) 7.028 0.976 1 0.3 (mildly flammable) 7.135 0.946 1 0.4 (mildly flammable) 7.146 0.915 1 0.5 (mildly flammable) 7.110 0.893 1 0.6 (non-flammable) 7.051 0.882 1 0.7 (non-flammable) 6.973 0.881 1 0.8 (non-flammable) 6.866 0.885 1 0.9 (non-flammable) 6.715 0.891 1 1 (non-flammable) 6.504 0.892 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.6 to 0.9 (60 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-5-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (flammable) 0.571 1.265 1 0.1 (mildly flammable) 0.595 1.252 1 0.2 (mildly flammable) 0.604 1.218 1 0.3 (mildly flammable) 0.601 1.174 1 0.4 (mildly flammable) 0.590 1.130 1 0.5 (mildly flammable) 0.576 1.093 1 0.6 (non-flammable) 0.561 1.066 1 0.7 (non-flammable) 0.545 1.048 1 0.8 (non-flammable) 0.528 1.036 1 0.9 (non-flammable) 0.510 1.028 1 1 (non-flammable) 0.489 1.019 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.1 to 0.9 (10 to 90 mol %), and more preferably 0.6 to 0.9 (60 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-6 (FO1216+HFO1132a)

TABLE 2-6-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0.79 (non-flammable) 1.820 1.332 1 0.8 (non-flammable) 1.769 1.308 1 0.9 (non-flammable) 1.315 1.090 1 0.93 (non-flammable) 1.202 1.032 1 0.94 (non-flammable) 1.167 1.013 1 0.95 (non-flammable) 1.133 0.995 1 1 (non-flammable) 0.979 0.912 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.79 to 0.95 (79 to 95 mol %), and more preferably 0.79 to 0.94 (79 to 94 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-6-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0.83 (non-flammable) 0.649 1.245 1 0.84 (non-flammable) 0.632 1.228 1 0.85 (non-flammable) 0.615 1.210 1 0.9 (non-flammable) 0.535 1.124 1 0.95 (non-flammable) 0.465 1.043 1 0.96 (non-flammable) 0.452 1.028 1 0.97 (non-flammable) 0.439 1.013 1 0.98 (non-flammable) 0.427 0.998 1 0.99 (non-flammable) 0.415 0.983 1 1 (non-flammable) 0.404 0.968 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.83 to 0.99 (83 to 99 mol %), and more preferably 0.83 to 0.9 (83 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-6-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0.79 (non-flammable) 12.757 1.480 1 0.8 (non-flammable) 12.384 1.444 1 0.9 (non-flammable) 8.986 1.121 1 0.93 (non-flammable) 8.138 1.042 1 0.94 (non-flammable) 7.875 1.018 1 0.95 (non-flammable) 7.623 0.995 1 1 (non-flammable) 6.504 0.892 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.79 to 0.95 (79 to 95 mol %), and more preferably 0.79 to 0.94 (79 to 94 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-6-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0.79 (non-flammable) 0.815 1.212 1 0.8 (non-flammable) 0.796 1.205 1 0.9 (non-flammable) 0.625 1.126 1 0.97 (non-flammable) 0.527 1.055 1 0.98 (non-flammable) 0.514 1.043 1 0.99 (non-flammable) 0.501 1.032 1 1 (non-flammable) 0.489 1.019 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.79 to 0.99 (79 to 99 mol %), and more preferably 0.79 to 0.98 (79 to 98 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 2-7 (FO1216+HFO1141)

TABLE 2-7-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0.42 (mildly flammable) 2.822 1.156 1 0.43 (mildly flammable) 2.826 1.181 1 0.5 (mildly flammable) 2.812 1.343 1 0.6 (mildly flammable) 2.647 1.498 1 0.7 (mildly flammable) 2.304 1.496 1 0.8 (mildly flammable) 1.834 1.338 1 0.9 (mildly flammable) 1.358 1.116 1 0.94 (non-flammable) 1.193 1.031 1 0.95 (non-flammable) 1.154 1.010 1 0.96 (non-flammable) 1.117 0.990 1 1 (non-flammable) 0.979 0.912 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.42 to 0.96 (42 to 96 mol %), and more preferably 0.94 to 0.96 (94 to 96 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-7-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0.53 (mildly flammable) 1.092 1.319 1 0.54 (mildly flammable) 1.088 1.336 1 0.6 (mildly flammable) 1.043 1.414 1 0.7 (mildly flammable) 0.911 1.436 1 0.8 (mildly flammable) 0.732 1.329 1 0.9 (mildly flammable) 0.553 1.151 1 0.94 (non-flammable) 0.489 1.077 1 0.95 (non-flammable) 0.474 1.059 1 0.96 (non-flammable) 0.459 1.041 1 0.97 (non-flammable) 0.445 1.022 1 0.98 (non-flammable) 0.431 1.004 1 0.99 (non-flammable) 0.417 0.986 1 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.53 to 0.99 (53 to 99 mol %), and more preferably 0.94 to 0.98 (94 to 98 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-7-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0.42 (mildly flammable) 18.994 1.240 1 0.43 (mildly flammable) 19.020 1.270 1 0.5 (mildly flammable) 18.991 1.479 1 0.6 (mildly flammable) 18.119 1.707 1 0.7 (mildly flammable) 16.062 1.725 1 0.8 (mildly flammable) 12.878 1.491 1 0.9 (mildly flammable) 9.324 1.158 1 0.94 (non-flammable) 8.069 1.039 1 0.95 (non-flammable) 7.781 1.012 1 0.96 (non-flammable) 7.504 0.986 1 1 (non-flammable) 6.504 0.892 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.42 to 0.96 (42 to 96 mol %), and more preferably 0.94 to 0.96 (94 to 96 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 2-7-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (mildly flammable) 2.342 0.871 1 0.42 (mildly flammable) 1.568 1.078 1 0.43 (mildly flammable) 1.554 1.090 1 0.44 (mildly flammable) 1.539 1.102 1 0.5 (mildly flammable) 1.438 1.163 1 0.6 (mildly flammable) 1.233 1.228 1 0.7 (mildly flammable) 1.017 1.246 1 0.8 (mildly flammable) 0.816 1.219 1 0.9 (mildly flammable) 0.641 1.147 1 0.94 (non-flammable) 0.578 1.104 1 0.95 (non-flammable) 0.563 1.091 1 0.96 (non-flammable) 0.548 1.078 1 0.97 (non-flammable) 0.533 1.065 1 0.98 (non-flammable) 0.518 1.050 1 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.42 to 0.98 (42 to 98 mol %), and more preferably 0.94 to 0.98 (94 to 98 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 3-1 (FO1216+HFC125)

TABLE 3-1-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (non-flammable) 1.637 0.850 3500 0.1 (non-flammable) 1.574 0.852 3073 0.2 (non-flammable) 1.510 0.855 2667 0.3 (non-flammable) 1.444 0.860 2279 0.4 (non-flammable) 1.377 0.866 1908 0.5 (non-flammable) 1.309 0.872 1555 0.6 (non-flammable) 1.240 0.879 1219 0.7 (non-flammable) 1.168 0.885 893 0.8 (non-flammable) 1.097 0.891 585 0.9 (non-flammable) 1.023 0.897 288 0.92 (non-flammable) 1.007 0.899 228 0.93 (non-flammable) 1.000 0.899 200 0.94 (non-flammable) 0.993 0.900 172 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.94 (80 to 94 mol %), and more preferably 0.935 to 0.94 (93.5 to 94 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-1-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (non-flammable) 0.667 0.871 3500 0.1 (non-flammable) 0.641 0.873 3073 0.2 (non-flammable) 0.614 0.876 2667 0.3 (non-flammable) 0.588 0.882 2279 0.4 (non-flammable) 0.561 0.889 1908 0.5 (non-flammable) 0.534 0.898 1555 0.6 (non-flammable) 0.507 0.907 1219 0.7 (non-flammable) 0.478 0.916 893 0.8 (non-flammable) 0.450 0.924 585 0.9 (non-flammable) 0.420 0.933 288 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-1-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (non-flammable) 10.746 0.846 3500 0.1 (non-flammable) 10.352 0.848 3073 0.2 (non-flammable) 9.944 0.852 2667 0.3 (non-flammable) 9.522 0.856 2279 0.4 (non-flammable) 9.089 0.861 1908 0.5 (non-flammable) 8.648 0.866 1555 0.6 (non-flammable) 8.199 0.872 1219 0.7 (non-flammable) 7.732 0.878 893 0.8 (non-flammable) 7.255 0.883 585 0.9 (non-flammable) 6.759 0.887 288 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-1-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (non-flammable) 0.993 0.915 3500 0.1 (non-flammable) 0.938 0.913 3073 0.2 (non-flammable) 0.881 0.913 2667 0.3 (non-flammable) 0.824 0.914 2279 0.4 (non-flammable) 0.767 0.917 1908 0.5 (non-flammable) 0.712 0.922 1555 0.6 (non-flammable) 0.661 0.928 1219 0.7 (non-flammable) 0.612 0.935 893 0.8 (non-flammable) 0.567 0.942 585 0.9 (non-flammable) 0.525 0.949 288 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 3-2 (FO1216+HFC143a)

TABLE 3-2-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (mildly flammable) 1.643 0.912 4470 0.1 (mildly flammable) 1.568 0.909 3728 0.2 (mildly flammable) 1.490 0.907 3089 0.3 (mildly flammable) 1.418 0.905 2535 0.4 (non-flammable) 1.347 0.904 2043 0.5 (non-flammable) 1.277 0.903 1605 0.6 (non-flammable) 1.209 0.903 1217 0.7 (non-flammable) 1.142 0.903 868 0.8 (non-flammable) 1.076 0.903 551 0.9 (non-flammable) 1.012 0.903 265 0.91 (non-flammable) 1.004 0.903 233 0.92 (non-flammable) 0.998 0.903 207 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.92 (80 to 92 mol %), and more preferably 0.9 to 0.92 (90 to 92 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-2-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (mildly flammable) 0.696 0.965 4470 0.1 (mildly flammable) 0.660 0.959 3728 0.2 (mildly flammable) 0.626 0.954 3089 0.3 (mildly flammable) 0.593 0.950 2535 0.4 (non-flammable) 0.562 0.947 2043 0.5 (non-flammable) 0.531 0.944 1605 0.6 (non-flammable) 0.501 0.943 1217 0.7 (non-flammable) 0.473 0.942 868 0.8 (non-flammable) 0.445 0.941 551 0.9 (non-flammable) 0.417 0.941 265 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-2-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (mildly flammable) 10.451 0.883 4470 0.1 (mildly flammable) 10.006 0.883 3728 0.2 (mildly flammable) 9.571 0.883 3089 0.3 (mildly flammable) 9.145 0.884 2535 0.4 (non-flammable) 8.723 0.884 2043 0.5 (non-flammable) 8.305 0.886 1605 0.6 (non-flammable) 7.894 0.887 1217 0.7 (non-flammable) 7.485 0.888 868 0.8 (non-flammable) 7.074 0.889 551 0.9 (non-flammable) 6.663 0.890 265 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-2-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (mildly flammable) 1.083 1.029 4470 0.1 (mildly flammable) 1.003 1.017 3728 0.11 (mildly flammable) 0.996 1.016 3661 0.2 (mildly flammable) 0.927 1.007 3089 0.26 (mildly flammable) 0.885 1.001 2749 0.27 (mildly flammable) 0.877 1.000 2691 0.28 (mildly flammable) 0.870 0.999 2638 0.3 (mildly flammable) 0.856 0.998 2535 0.4 (non-flammable) 0.789 0.989 2043 0.5 (non-flammable) 0.727 0.981 1605 0.6 (non-flammable) 0.669 0.974 1217 0.7 (non-flammable) 0.617 0.969 868 0.8 (non-flammable) 0.568 0.964 551 0.9 (non-flammable) 0.525 0.959 265 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 3-3 (FO1216+HFC32)

TABLE 3-3-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (mildly flammable) 2.545 0.959 675 0.1 (mildly flammable) 2.338 0.954 511 0.2 (non-flammable) 2.145 0.945 393 0.3 (non-flammable) 1.963 0.936 302 0.4 (non-flammable) 1.793 0.928 232 0.5 (non-flammable) 1.634 0.922 174 0.56 (non-flammable) 1.546 0.919 145 0.6 (non-flammable) 1.489 0.918 128 0.7 (non-flammable) 1.347 0.914 88 0.8 (non-flammable) 1.212 0.910 55 0.9 (non-flammable) 1.078 0.905 26 0.95 (non-flammable) 1.013 0.904 13 0.96 (non-flammable) 0.998 0.904 10 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.3 to 0.96 (30 to 96 mol %), and more preferably 0.56 to 0.96 (56 to 96 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-3-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 1430 0 (mildly flammable) 1.135 1.052 675 0.1 (mildly flammable) 1.032 1.040 511 0.13 (non-flammable) 1.003 1.035 472 0.14 (non-flammable) 0.993 1.034 460 0.2 (non-flammable) 0.937 1.024 393 0.3 (non-flammable) 0.849 1.007 302 0.33 (non-flammable) 0.824 1.002 279 0.34 (non-flammable) 0.815 1.000 272 0.35 (non-flammable) 0.808 0.999 265 0.4 (non-flammable) 0.768 0.991 232 0.5 (non-flammable) 0.694 0.979 174 0.56 (non-flammable) 0.653 0.973 145 0.6 (non-flammable) 0.626 0.969 128 0.7 (non-flammable) 0.563 0.961 88 0.8 (non-flammable) 0.503 0.953 55 0.9 (non-flammable) 0.446 0.946 26 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.3 to 0.9 (30 to 90 mol %), and more preferably 0.56 to 0.9 (56 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-3-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (mildly flammable) 15.591 0.899 675 0.1 (mildly flammable) 14.442 0.899 511 0.2 (non-flammable) 13.368 0.897 393 0.3 (non-flammable) 12.348 0.894 302 0.4 (non-flammable) 11.383 0.892 232 0.5 (non-flammable) 10.472 0.891 174 0.56 (non-flammable) 9.956 0.892 145 0.6 (non-flammable) 9.622 0.892 128 0.7 (non-flammable) 8.781 0.894 88 0.8 (non-flammable) 7.959 0.893 55 0.9 (non-flammable) 7.105 0.891 26 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.3 to 0.9 (30 to 90 mol %), and more preferably 0.56 to 0.9 (56 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-3-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 2088 0 (mildly flammable) 1.749 1.101 675 0.1 (mildly flammable) 1.583 1.102 511 0.2 (non-flammable) 1.421 1.091 393 0.3 (non-flammable) 1.261 1.073 302 0.4 (non-flammable) 1.110 1.053 232 0.47 (non-flammable) 1.011 1.040 190 0.48 (non-flammable) 0.998 1.038 185 0.5 (non-flammable) 0.970 1.034 174 0.56 (non-flammable) 0.894 1.023 145 0.6 (non-flammable) 0.846 1.015 128 0.68 (non-flammable) 0.754 1.001 95 0.69 (non-flammable) 0.744 1.000 92 0.7 (non-flammable) 0.733 0.998 88 0.8 (non-flammable) 0.638 0.984 55 0.9 (non-flammable) 0.556 0.971 26 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.3 to 0.9 (30 to 90 mol %), and more preferably 0.56 to 0.9 (56 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 3-4 (FO1216+HFC134a)

TABLE 3-4-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (non-flammable) 1.000 1.000 1430 0.1 (non-flammable) 1.022 0.988 1230 0.2 (non-flammable) 1.038 0.977 1046 0.3 (non-flammable) 1.047 0.965 877 0.4 (non-flammable) 1.051 0.954 723 0.5 (non-flammable) 1.047 0.944 580 0.6 (non-flammable) 1.038 0.934 447 0.7 (non-flammable) 1.023 0.925 324 0.8 (non-flammable) 1.002 0.917 208 0.81 (non-flammable) 1.000 0.916 198 0.9 (non-flammable) 0.977 0.910 101 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-4-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (non-flammable) 0.436 1.085 1430 0.1 (non-flammable) 0.443 1.068 1230 0.2 (non-flammable) 0.447 1.050 1046 0.3 (non-flammable) 0.448 1.033 877 0.4 (non-flammable) 0.447 1.016 723 0.49 (non-flammable) 0.444 1.002 593 0.5 (non-flammable) 0.443 1.000 580 0.51 (non-flammable) 0.443 0.999 565 0.6 (non-flammable) 0.437 0.986 447 0.7 (non-flammable) 0.428 0.972 324 0.8 (non-flammable) 0.417 0.960 208 0.9 (non-flammable) 0.404 0.950 101 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-4-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (non-flammable) 6.352 0.947 1430 0.1 (non-flammable) 6.518 0.940 1230 0.2 (non-flammable) 6.643 0.933 1046 0.3 (non-flammable) 6.728 0.926 877 0.4 (non-flammable) 6.772 0.920 723 0.5 (non-flammable) 6.777 0.914 580 0.6 (non-flammable) 6.743 0.908 447 0.7 (non-flammable) 6.671 0.903 324 0.8 (non-flammable) 6.562 0.898 208 0.9 (non-flammable) 6.420 0.896 101 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-4-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (non-flammable) 0.526 1.146 1430 0.1 (non-flammable) 0.538 1.124 1230 0.2 (non-flammable) 0.548 1.102 1046 0.3 (non-flammable) 0.555 1.081 877 0.4 (non-flammable) 0.558 1.061 723 0.5 (non-flammable) 0.556 1.041 580 0.6 (non-flammable) 0.550 1.022 447 0.7 (non-flammable) 0.539 1.004 324 0.71 (non-flammable) 0.538 1.002 311 0.72 (non-flammable) 0.536 1.000 300 0.73 (non-flammable) 0.535 0.998 288 0.8 (non-flammable) 0.524 0.986 208 0.9 (non-flammable) 0.505 0.970 101 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.72 to 0.9 (72 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 3-5 (FO1216+HFC152a)

TABLE 3-5-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (flammable) 0.954 1.037 124 0.1 (flammable) 0.971 1.026 99 0.2 (flammable) 0.984 1.015 79 0.3 (flammable) 0.993 1.002 63 0.31 (flammable) 0.994 1.001 62 0.32 (flammable) 0.994 1.000 60 0.33 (flammable) 0.995 0.999 59 0.4 (flammable) 0.998 0.989 50 0.5 (mildly flammable) 1.000 0.976 39 0.6 (mildly flammable) 0.997 0.961 29 0.7 (non-flammable) 0.991 0.947 21 0.8 (non-flammable) 0.980 0.932 13 0.9 (non-flammable) 0.965 0.915 7 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.5 to 0.9 (50 to 90 mol %), and more preferably 0.5 to 0.8 (50 to 80 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-5-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (flammable) 0.424 1.142 124 0.1 (flammable) 0.429 1.126 99 0.2 (flammable) 0.432 1.108 79 0.3 (flammable) 0.433 1.089 63 0.4 (flammable) 0.432 1.068 50 0.5 (mildly flammable) 0.430 1.047 39 0.6 (mildly flammable) 0.425 1.025 29 0.7 (non-flammable) 0.419 1.004 21 0.71 (non-flammable) 0.418 1.001 20 0.72 (non-flammable) 0.417 0.999 19 0.8 (non-flammable) 0.411 0.982 13 0.9 (non-flammable) 0.401 0.961 7 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.5 to 0.9 (50 to 90 mol %), and more preferably 0.5 to 0.8 (50 to 80 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-5-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (flammable) 5.943 0.967 124 0.1 (flammable) 6.075 0.962 99 0.2 (flammable) 6.186 0.956 79 0.3 (flammable) 6.276 0.949 63 0.4 (flammable) 6.344 0.941 50 0.5 (mildly flammable) 6.389 0.933 39 0.6 (mildly flammable) 6.409 0.925 29 0.7 (non-flammable) 6.405 0.916 21 0.8 (non-flammable) 6.376 0.908 13 0.9 (non-flammable) 6.323 0.898 7 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.5 to 0.9 (50 to 90 mol %), and more preferably 0.5 to 0.8 (50 to 80 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-5-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (flammable) 0.532 1.212 124 0.1 (flammable) 0.539 1.195 99 0.2 (flammable) 0.545 1.174 79 0.3 (flammable) 0.547 1.152 63 0.4 (flammable) 0.548 1.127 50 0.5 (mildly flammable) 0.545 1.101 39 0.6 (mildly flammable) 0.539 1.073 29 0.7 (non-flammable) 0.530 1.044 21 0.8 (non-flammable) 0.518 1.014 13 0.84 (non-flammable) 0.512 1.003 10 0.85 (non-flammable) 0.510 1.000 10 0.86 (non-flammable) 0.509 0.997 9 0.9 (non-flammable) 0.503 0.985 7 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.5 to 0.9 (50 to 90 mol %), and more preferably 0.5 to 0.85 (50 to 85 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 3-6 (FO1216+HFC227ea)

TABLE 3-6-1 R134a Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R134a COP vs. R134a GWP (Comparison) R134a 1.000 1.000 1430 0 (non-flammable) 0.613 0.929 3220 0.1 (non-flammable) 0.650 0.926 2934 0.2 (non-flammable) 0.686 0.923 2641 0.3 (non-flammable) 0.722 0.920 2338 0.4 (non-flammable) 0.757 0.917 2029 0.5 (non-flammable) 0.791 0.913 1714 0.6 (non-flammable) 0.824 0.911 1388 0.7 (non-flammable) 0.857 0.908 1054 0.8 (non-flammable) 0.888 0.906 712 0.9 (non-flammable) 0.919 0.255 362 1 (non-flammable) 0.947 0.904 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-6-2 R410A Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R410A COP vs. R410A GWP (Comparison) R410A 1.000 1.000 2088 0 (non-flammable) 0.254 0.975 3220 0.1 (non-flammable) 0.269 0.971 2934 0.2 (non-flammable) 0.284 0.966 2641 0.3 (non-flammable) 0.298 0.962 2338 0.4 (non-flammable) 0.312 0.958 2029 0.5 (non-flammable) 0.326 0.954 1714 0.6 (non-flammable) 0.340 0.950 1388 0.7 (non-flammable) 0.353 0.946 1054 0.8 (non-flammable) 0.366 0.944 712 0.9 (non-flammable) 0.378 0.942 362 1 (non-flammable) 0.390 0.941 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-6-3 R123 Large Air Conditioner Comparison/ FO1216 Molar Ratio CAP vs. R123 COP vs. R123 GWP (Comparison) R123 1.000 1.000 77 0 (non-flammable) 4.072 0.911 3220 0.1 (non-flammable) 4.321 0.909 2934 0.2 (non-flammable) 4.563 0.907 2641 0.3 (non-flammable) 4.800 0.905 2338 0.4 (non-flammable) 5.029 0.903 2029 0.5 (non-flammable) 5.251 0.900 1714 0.6 (non-flammable) 5.466 0.898 1388 0.7 (non-flammable) 5.675 0.895 1054 0.8 (non-flammable) 5.875 0.894 712 0.9 (non-flammable) 6.065 0.892 362 1 (non-flammable) 6.246 0.891 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

TABLE 3-6-4 R404A Refrigerator-Freezer Comparison/ FO1216 Molar Ratio CAP vs. R404A COP vs. R404A GWP (Comparison) R404A 1.000 1.000 3922 0 (non-flammable) 0.272 0.981 3220 0.1 (non-flammable) 0.290 0.977 2934 0.2 (non-flammable) 0.309 0.972 2641 0.3 (non-flammable) 0.329 0.967 2338 0.4 (non-flammable) 0.350 0.963 2029 0.5 (non-flammable) 0.372 0.960 1714 0.6 (non-flammable) 0.395 0.957 1388 0.7 (non-flammable) 0.418 0.956 1054 0.8 (non-flammable) 0.441 0.955 712 0.9 (non-flammable) 0.463 0.955 362 1 (non-flammable) 0.485 0.956 1

As is clear from the table above, the molar ratio of FO-1216, in relation to the predetermined effects of the present disclosure, is preferably within the range of 0.8 to 0.9 (80 to 90 mol %), and more preferably 0.85 to 0.9 (85 to 90 mol %) in 100 mol % of the refrigerant component of the refrigerant composition.

Embodiment 4-1 (FO1216+“HFO+HFC”)

TABLE 4-1 Mol % Flammable CAP COP CAP COP CAP COP CAP COP HFO-1234ze FO-1216 HFC-227ea HFC-134a GWP or Not vs. R134a vs. R410A vs. R123 vs. R404A 93 3 2 3 136 Non-flammable 0.759 0.993 0.327 1.069 4.873 0.947 0.378 1.121 95 2 2 1 123 Non-flammable 0.750 0.994 0.324 1.071 4.815 0.947 0.373 1.123

The refrigerant compositions shown in the table above have a low GWP; are non-flammable or mildly flammable; and have a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

Embodiment 4-2 (FO1216+“HFO+HFE”)

TABLE 4-2 Mol % Flammable CAP COP CAP COP CAP COP CAP COP HFO-1234ze FO-1216 HFE-227me GWP or Not vs. R134a vs. R410A vs. R123 vs. R404A 96 2 2 45 Non-flammable 0.741 1.004 0.321 1.083 4.746 0.955 0.375 1.147 89 5 6 143 Non-flammable 0.742 0.995 0.320 1.070 4.775 0.950 0.367 1.127

The refrigerant compositions shown in the table above have a low GWP; are non-flammable or mildly flammable; and have a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

Embodiment 4-3 (FO1216+“Halogenated Ethylene+HFC”)

TABLE 4-3 Mol % Flammable CAP COP CAP COP CAP COP CAP COP HFO-1132E FO-1216 HFC-32 GWP or Not vs. R134a vs. R410A vs. R123 vs. R404A 20.9 53.4 25.7 85 Non-flammable 1.563 0.909 0.656 0.959 10.107 0.886 0.900 1.005

The refrigerant composition shown in the table above has a low GWP; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

Embodiment 4-4 (FO1216+“Halogenated Ethylene+HFC”)

TABLE 4-4 Mol % Flammable CAP COP CAP COP CAP COP CAP COP HFO-1123 FO-1216 HFC-32 GWP or Not vs. R134a vs. R410A vs. R123 vs. R404A 19.5 49.8 30.7 102 Non-flammable 1.634 0.903 0.685 0.951 10.573 0.880 0.937 0.995

The refrigerant composition shown in the table above has a low GWP; is non-flammable or mildly flammable; and has a refrigerating capacity (Cap) and/or coefficient of performance (COP) equivalent to or higher than those of traditional refrigerants, such as R-134a, R-410A, R-123, or R-404A, when used as an alternative refrigerant for these traditional refrigerants.

DESCRIPTION OF REFERENCE SYMBOLS

-   A. charging line -   B. sampling line -   C. thermometer -   D. pressure gauge -   E. electrode -   F. stirring blade (made of PTFE) 

The invention claimed is:
 1. A refrigerant composition comprising FO-1216, HFO-1234yf, and HFO-1132(E).
 2. The refrigerant composition according to claim 1, wherein the HFO-1234yf is present in an amount of 50 mol % or more. 